How to Maintain Coal/ Biomass Fired Chain Grate Steam Boiler01/18/2017
New type DZL series boiler is the single drum longitudinal type water and fire tube shell boiler, the combustion equipment is chain grate. Both sides of the furnace water wall are radiation heating surface, two wings of the furnace are convective heating surface. The thread smoke tube convective heating surface is laid out in the inner drum. The furnace wall adopts the new technology of whole pouring molding by using heat resistant concrete. This series of boiler adopts latest scientific research achievements, such as arched tube plate, thread smokestacks, and splayed tube bank, etc. It has the advantages of low stress, high thermal efficiency, stable operation, convenient adjustment, sufficient output, wide adaptability of various coals, and environmental protection.
Then How to Maintain Coal/Biomass Fired Steam Boiler?
1. Avoid burn out coal gate, observation door, and fire draw door, smoke spraying in furnace and positive pressure combustion are not allowed.
2. Shut down boiler for maintenance within 24 hours if the front arch is break off.
3. Check the front axle and the rear axle of the chain, if there is lubricating oil leakage in oil cup, fans, and axle pedestal of reducer, each shift should add oil in time.
4. In case of the occurrence of severe vibration of induced draft fan, stop and check. Generally, the fan should be transposed if it is caused by internal wear of impeller.
5. Check whether there is stuck phenomenon for slag extractor, too much slag is not allowed in slag hopper.
6. Impounded surface water is better not to occur under the boiler bottom, to avoid the corrosion because of moist.
7. Boiler should be checked and repaired after 2-3 weeks operation, shut down and check once every 2-3 months.
8. Long-term shutdown boiler has dry and wet maintenance methods. The dry maintenance method is used for the boilers shutdown for more than one month, the wet maintenance method is used for the boilers shutdown for less than one month.
(1) Dry maintenance
Discharge water boiler, the internal dirt completely removed, rinse, and drying furnace with a slow fire, then the put diameter of 10-30 mm lump quicklime in the dish, placed in the drum, do not make contact with the metal lime. quicklime weight to 3 kgs per cubic meter drum volume calculations, then close all manholes, hand holes pipeline valve, inspected once every three months.Change it when quick lime crushed in pieces.
(2) Wet maintenance
Drain the boiler water off after shut down the boiler, thoroughly remove the internal dirt and rinse off the boiler, refill the treated water until full, heat the boiler water to 100℃, discharge the air out of the boiler, then chose all the valves. In the cold area, the wet maintenance method can not be used to avoid boiler damage caused by the boiler water.
The coal/biomass fired chain grate steam boiler is the national product of Zhongding Boiler, the patent number of 200920088278.3. Zhongding Boiler is the Chinese professional industrial boiler manufacturers, except the coal/biomass fired chain grate boiler, there are some other main products, such as oil gas fire tube stem generator, thermal oil boiler, waste heat boiler, circulating fluidized bed boiler, and industrial autoclave,etc.
12-05---4 Sets Horizontal Type Natural Gas Fired Hot Water
4 sets horizontal type natural gas fired hot water boilers are shipped to Korea. The models is CWNS-
01-18---Bangladesh Customer Visited Zhongding For Coal Fir
Bangladesh customer came to Zhongding Boiler for investigation in November. The boiler they prefer i