This series boiler uses the general combustion technique. The coal or biomass was feed by workers manually. It is mainly composed of furnace, seal ring, horizontal water tubes, circular flue, gauges, valves and chimney. After burning in the fire grate, the exhaust gas pass through the horizontal water tube, and the small carbon block and dust in the exhaust gas fall on the fire grate and re-burn. Then the exhaust gas is released to the air though the chimney.
|Supply water temperature (℃)||Return water temperature (℃)||Efficiency(%)||Heating area(㎡)||Overall Dimension (Φ×h) (m)||Reference weight(kg)||CLSG0.12-95/70||0.12||85||65||76||8.1||0.9×2.6||550||CLSG0.24-95/70||0.24||85||65||76||12.5||1.1×2.8||900||CLSG0.35-95/70||0.35||85||65||76||19.2||1.2×3.4||1893||CLSG0.5-95/70||0.5||85||65||76||22.1||1.3×4||3120||CLSG0.6-95/70||0.6||85||65||76||24.3||1.4×4||3650||CLSG0.7-95/70||0.7||85||65||76||39.5||1.6×4||3821||CLSG1.05-95/70||1.05||85||65||76||48.8||1.8×5||4800||CLSG1.4-95/70||1.4||85||65||76||74.6||2×5.3||5700||CLSG2.1-95/70||2.1||85||65||76||109.4||2×5.5||7650||Note: Parameters is for reference only, if any change should follow actual drawings|